The pressure ratings given are for water, non-shock, @ 73°F. The following temperature de-rating factors are to be applied to the working pressure ratings listed when operating at elevated temperatures.
Multiply the working pressure rating of the selected pipe at 73°F, by the appropriate de-rating factor to determine the maximum working pressure rating of the pipe at the elevated temperature chosen.
EX: 10" CPVC SCH 80 @ 120°F = ?
230 psi x 0.65 = 149.5 psi max. @ 120°F
THE MAXIMUM SERVICE TEMPERATURE FOR CPVC IS 200°F.
Solvent cemented joints should be utilized when working at or near maximum temperatures. We do not recommend the use of CPVC for threaded connections at temperatures above 150°F; use flanged joints, unions, or roll grooved couplings where disassembly is necessary at elevated temperatures.
Threading of Sch 40 CPVC pipe is not a recommended practice due to insufficient wall thickness. Thread only Sch 80 or heavier walls.
Threading requires a 50% reduction in pressure rating stated for plain end pipe @73°F.